1. Things are easy to install:
Waller is usually out of warehouse quickly, easy to install in transportation and site, greatly shorten the construction machine, save installation costs, so as to produce boilers in time.
When the boiler is opened, the configuration is reasonable, the water circulation is smooth, the cooling is guaranteed when the boiler is opened, and the safety of the boiler is guaranteed.
3. Easy to manage:
Boiler steam pack can be installed and repaired with acceptance holes. The smoke box in front of the boiler is easy to open, and the personnel are convenient and clear, providing good conditions.
4. Complete combustion:
The second air and reasonable heating furnace design, full combustion of fuel, removal of black smoke.
5. Efficient Arrangement:
Boiler arrangement and biofuel suit to avoid air leakage and oil leakage. Compared with the general arrangement of heating stoves, the operation is convenient and has obvious advantages.
Main Technical Parameters of Series Biomass Steam Boiler
|Feed Water Temperature||℃||20||20||20||20||20||20||60|
Note: The fuel consumption in the table is calculated on the basis of the low calorific value of biomass particles 17084KJ/Kg (4085Kcal/Kg). If the low calorific value of biomass fuel is larger than that, the corresponding fuel consumption will be more economical than that in the table.
Shape and Interface Dimensions of Series Hand-fired Biomass Steam Boilers
|Rated Steam Capacity||t/h||1||2||3||4||6||8||10|
Host Transport Dimension
|Host Transport Weight||/||t||13.6||18||23||25.3||31||34||39|
|Main Steam Valve Pipe Diameter||DN||mm||65||80||100||100||125||150||150|
|Feed Water Valve||DN||mm||40||40||40||40||50||50||50|
|Safety Valve Diameter||DN||mm||2×40||2×50||2×50||2×50||50/80||2×80||2×80|
|Drain Valve Pipe Diameter||DN||mm||3×40||3×40||3×40||3×40||3×40||3×40||3×40|
Remarks: We will reserve rights to change the above mentioned data due to continuous policy transformation and product improvement.
|Contact Person :||furnacess|
|Tel :||+ 86 17733330123|