Series Double Drum Oil and Gas Fired Steam Boiler
Double boiler temperature and double boiler with two coils, T back vertical, high speed boiler. The types of pots include the upper and lower tubes, the ratio plates, the rim tubes and the capacitor. The fuel is burned in the pot and the pearl electricity is transferred from the transfer tube to the tube and heat exchanger. The future of mechatronics is China's work.
1. Suitable for all fuel:
The cleaning area is large and the fuel burns. It is suitable for low temperature aeration such as gas furnaces and blast furnaces. The calorie-burning fuel that consumes good cleaning, such as natural gas, natural gas, and more.
2. Load load:
The heating area is large, the furnace is large, the output is high and the storage capacity is adequate.
3. Effective structure:
The front water wall is placed in front of the pot to control the inclusion of the burner head to ensure the water is cooled and warmed by the burner, which helps to reduce the savings. of kitchen mixing and burning off oil.
4. Easy to hold:
The floor wall is covered with explosive doors, a fire pit, and surveillance doors. Boiler cabinets are provided with open packages before and after heating to ensure boiler protection.
5. Reducing heat reduction:
The use of thick textures reduces heat loss from the pot and increases the heat.
6. Long service life:
It is a professional design, advanced technology, by overseeing operations and quality control to ensure the quality of the pots. The kitchen has been a service provider for over 20 years.
Main Parameters of Series Oil & Gas Fired Steam Boiler
|Feed Water Temperature||℃||104||104||104||104||104||104||104|
|Fuel||/||Natural Gas, Liquefied Gas, City Gas, Light Oil|
|Fuel Consumption||Natural Gas||NM3/h||733||1098||1464||1829||2559||3662||4769|
|Gas Inlet Pressure||Natural Gas||Mbar||150-200||150-300||150-300||150-300||150-300||150-300||150-300|
Remarks: The fuel consumption in above table are counted the low calorific value of light oil as 42915 KJ/Kg(10260Kcal/Kg), the low calorific value of natural gas as 35588 KJ/NM3(8500Kcal/NM3), the low calorific value of liquefied oil as 45998 KJ/Kg(11000Kcal/Kg), the low calorific value of city gas as 16750 KJ/NM3(4000Kcal/NM3).
|L||mm||5633||6365||6665||Separated Transport||Separated Transport||Separated Transport||Separated Transport|
|Main Steam Valve Pipe Diameter||DN||mm||150||150||200||200||250||2×150||2×150|
|Feed Water Valve||DN||mm||50||65||65||80||100||125||125|
|Drain Valve Pipe Diameter||DN||mm||40||40||50||50||50||50||50|
External and Interface Dimension of Series Oil & Gas Fired Steam Boiler
Remarks: We will reserve rights to change the above mentioned data due to continuous policy transformation and product improvement.
|Contact Person :||Mr. furnacess|
|Tel :||+ 86 17733330123|