Series Double Drum Oil and Gas Fired Steam Boiler
Gas vapour boilers with double drums of the SZS series are two drums, long -running, fast -charging water heaters. The series of boilers consists of upper and lower drums, membrane walls, convection tubes and capacitors. Fuel burns in the boiler. The flue gas is discharged into the chimney from the convection pipes and the waste heat.
1. Miscellaneous fuels:
Furnace area is large, fuel combustion is sufficient, especially suitable for low -calorific fuels such as coke oven gas, blast furnace gas, etc. natural gas, liquefied gas, etc.
2. Overload capacity:
The heating area is large, the furnace area is large, the production is strong and has a certain overcharging capacity.
3. Reasonable structure:
The front water balance in front of the boiler is easy to repair the burner head, secure the water level and cool close to the burner, help remove the carbon storage in the burner and make the combustion more full.
4. Easy to maintain:
The explosion -proof door, fire -proof holes and inspection door are mounted on the boiler wall and the inspection hall is mounted on the front and rear of the boiler to facilitate the inspection of the boiler.
5. Reducing heat output:
A thin layer of insulation is used to reduce the heat sink of boilers and improve heat efficiency.
6. Long life and durability:
An excellent professional design, advanced production technology, strict quality control and control are the quality assurance of each boiler. The normal life of the boiler is over twenty years.
Main Parameters of Series Oil & Gas Fired Steam Boiler
|Feed Water Temperature||℃||104||104||104||104||104||104||104|
|Fuel||/||Natural Gas, Liquefied Gas, City Gas, Light Oil|
|Fuel Consumption||Natural Gas||NM3/h||733||1098||1464||1829||2559||3662||4769|
|Gas Inlet Pressure||Natural Gas||Mbar||150-200||150-300||150-300||150-300||150-300||150-300||150-300|
Remarks: The fuel consumption in above table are counted the low calorific value of light oil as 42915 KJ/Kg(10260Kcal/Kg), the low calorific value of natural gas as 35588 KJ/NM3(8500Kcal/NM3), the low calorific value of liquefied oil as 45998 KJ/Kg(11000Kcal/Kg), the low calorific value of city gas as 16750 KJ/NM3(4000Kcal/NM3).
|L||mm||5633||6365||6665||Separated Transport||Separated Transport||Separated Transport||Separated Transport|
|Main Steam Valve Pipe Diameter||DN||mm||150||150||200||200||250||2×150||2×150|
|Feed Water Valve||DN||mm||50||65||65||80||100||125||125|
|Drain Valve Pipe Diameter||DN||mm||40||40||50||50||50||50||50|
External and Interface Dimension of Series Oil & Gas Fired Steam Boiler
Remarks: We will reserve rights to change the above mentioned data due to continuous policy transformation and product improvement.