Series Double Drum Oil and Gas Fired Steam Boiler
The steam boilers of the series are double drums, longitudinal -D series, fast steam boilers. The boiler series consists of upper and lower drums, membrane walls, convection pipes and capacitors. Fuel is burned in the boiler. Liquid gas is piped from the convection pipes into the chimney and waste heat recovery plant. With the mechatronic structure, the performance in China is leading.
1. Miscellaneous fuels:
The range of furnaces is large, the combustion of fuels is sufficient, especially suitable for low -calorific fuels such as coke oven gases, blast furnace gas, etc. The combustion efficiency of high -calorific fuels is better, such as natural gas, liquefied gas, etc.
2. Overload capacity:
The heating area is large, the furnace area is large, the power is strong and has a certain overcharging capacity.
3. Appropriate structure:
The front water wall in front of the boiler is easy to fix the burner head, ensure the water level and cooling near the burner, eliminate the carbon stock in the burner and complete the combustion of the fuel.
4. Easy maintenance:
The explosion -proof door, the fire -resistant hole and the overhaul door are mounted on the wall of the boiler and the overhaul hole is placed on the front and back of the boiler water to facilitate the overhaul of the boiler.
5. Reduction of heat loss:
A thick insulation layer is used to reduce the heat loss of the boiler and to improve the heat efficiency.
6. Long service life and durability:
Excellent professional design, advanced manufacturing technology, strict quality control and control are the quality assurance of each boiler. The normal life of the boiler is more than 20 -years.
Main Parameters of Series Oil & Gas Fired Steam Boiler
|Feed Water Temperature||℃||104||104||104||104||104||104||104|
|Fuel||/||Natural Gas, Liquefied Gas, City Gas, Light Oil|
|Fuel Consumption||Natural Gas||NM3/h||733||1098||1464||1829||2559||3662||4769|
|Gas Inlet Pressure||Natural Gas||Mbar||150-200||150-300||150-300||150-300||150-300||150-300||150-300|
Remarks: The fuel consumption in above table are counted the low calorific value of light oil as 42915 KJ/Kg(10260Kcal/Kg), the low calorific value of natural gas as 35588 KJ/NM3(8500Kcal/NM3), the low calorific value of liquefied oil as 45998 KJ/Kg(11000Kcal/Kg), the low calorific value of city gas as 16750 KJ/NM3(4000Kcal/NM3).
|L||mm||5633||6365||6665||Separated Transport||Separated Transport||Separated Transport||Separated Transport|
|Main Steam Valve Pipe Diameter||DN||mm||150||150||200||200||250||2×150||2×150|
|Feed Water Valve||DN||mm||50||65||65||80||100||125||125|
|Drain Valve Pipe Diameter||DN||mm||40||40||50||50||50||50||50|
External and Interface Dimension of Series Oil & Gas Fired Steam Boiler
Remarks: We will reserve rights to change the above mentioned data due to continuous policy transformation and product improvement.
|Contact Person :||furnacess|
|Tel :||+ 86 17733330123|